Be the first to write a review. Approx dimensions are mm wide x 38mm high x 85mm deep. Fits a hole cut out of mm x 30mm. This controller is volt, it is supplied with a front cover and clips as shown, it does not include a probe, this controller uses an NTC type probe. Please visit our ebay shop to see our huge range of catering parts. All of our parts are sent out same day from our own warehouse stock.
|Published (Last):||12 October 2007|
|PDF File Size:||4.29 Mb|
|ePub File Size:||3.91 Mb|
|Price:||Free* [*Free Regsitration Required]|
Quick Links. Download this manual. This manual is part of the product and should be kept near the instrument for easy and quick reference. The instrument shall not be used for purposes different from those described hereunder.
It cannot be. Check the supply voltage is correct before connecting the instrument. Do not expose to water or moisture: use the controller only within the operating limits avoiding sudden. Warning: disconnect all electrical connections before any kind of maintenance. Fit the probe where it is not accessible by the End User. The instrument must not be opened. In case of failure or faulty operation send the instrument back to the distributor or to "Dixell s.
Consider the maximum current which can be applied to each relay see Technical Data. Ensure that the wires for probes, loads and the power supply are separated and far enough from each. In case of applications in industrial environments, the use of mains filters our mod.
FT1 in parallel with. Model XWL, 38x mm format, is microprocessor based controller suitable for applications on medium or. It is provided with four relay outputs to control compressor, defrost - which. It is also provided with three NTC probe inputs, one for temperature control, one to control the defrost end.
There are two digital inputs free contact. RTU compatible monitoring system and to programme the parameter list with the "Hot Key". The regulation is performed according to the temperature measured by the thermostat probe with a positive.
In case of fault in the thermostat probe the start and stop of the compressor are timed through parameters. When defrost is not in progress, it can be activated the keypad by holding the. The compressor operates in continuous mode for the time set through the "CCt" parameter. The cycle. Three defrost modes are available through the "tdF" parameter: defrost with electrical heater, hot gas or. At the end of defrost the drip time is controlled through the "Fdt" parameter.
The fan control mode is selected by means of the "FnC" parameter:. After defrost, there is a timed fan delay allowing for drip time, set by means of the "Fnd" parameter. An additional parameter "FSt" provides the setting of temperature, detected by the evaporator probe, above. This can be used to make sure circulation of air only if his temperature is lower. To display and modify target set point; in programming mode it selects a parameter or confirm an.
By holding it pressed for 3s when max or min temperature is displayed it will be erased. To see the max. By holding it pressed for 3s the fast freezing cycle is started. To see the min stored temperature; in programming mode it browses the parameter codes or. By holding it pressed for 3s the defrost is started. Each LED function is described in the following table. Function of the LEDs placed on the left top side of buttons:. The "Lo" message will be displayed followed by the minimum temperature recorded.
The "Hi" message will be displayed followed by the maximum temperature recorded. To reset the stored temperature, when max or min temperature is displayed :. Push and immediately release the SET key: the display will show the Set point value;.
To memorise the new set point value push the SET key again or wait 10s. Push the DEF key for more than 2 seconds and a manual defrost will start. To enter the parameter list "Pr1" user accessible parameters operate as follows:. The instrument will show the first parameter present in "Pr1".
Table of Contents. Print page 1 Print document 4 pages. Cancel Delete. Sign In OR. Don't have an account? Sign up! Restore password. Upload from disk. Upload from URL.
CONTROLLER DIXELL XW260L-5N0C5
electronic controller DIXELL XW260L-5N0C0 402036
electronic controller DIXELL XW260L-5N0C0 mounting measurements 150x30mm
dixell WING XW60L Installing And Operating Instructions